Plumbing fixtures, drains, appurtenances and appliances used to receive or discharge liquid waste or sewage shall be directly connected to the sanitary drainage system of the building or premises, in accordance with the requirements of this code. Bell holes, hub holes and coupling holes shall be provided at points where the pipe is joined. If the system is tested in sections, each opening shall be tightly plugged except the highest openings of the section under test, and each section shall be filled with water, but no section shall be tested with less than a 10-foot 3048 mm head of water. The code official shall require the removal of any if necessary to ascertain whether the pressure has reached all parts of the system. A is guilty of the offence defined in this section. Such shield plates shall have a thickness of not less than 0.
Scuppers shall be sized to prevent the depth of ponding water from exceeding that for which the roof was designed as determined by. Equipment efficiencies shall be in accordance with the. Causing death of quick unborn child by act amounting to culpable homicide:- whoever does any act under such circumstances, that if he thereby caused death he would be guilty of culpable homicide, and does by such act cause the death of a quick unborn child, shall be punished with imprisonment of either description for a term which may extend to ten years, and shall also be liable to fine. Amendment by applicable toplaced in service after Dec. The annular space between the outside of a pipe and the inside of a pipe sleeve or between the outside of a pipe and an opening in a building envelope wall, floor, or ceiling assembly penetrated by a pipe shall be sealed in an approved manner with caulking material, foam sealant or closed with a gasketing system.
In testing successive sections, at least the upper 10 feet 3048 mm of the next preceding section shall be tested so that no joint or pipe in the building, except the uppermost 10 feet 3048 mm of the system, shall have been submitted to a test of less than a 10-foot 3048 mm head of water. Each length of pipe and each pipe fitting, trap, fixture, material and device utilized in a plumbing system shall bear the identification of the manufacturer and any markings required by the applicable referenced standards. Explanation:- A woman who causes herself to miscarry, is within the meaning of this section. Effective Date of 1989 Amendment Amendment by applicable to costsinbeginning after Dec. If the alternative engineered design is not approved, the code official shall notify the registered design professional in writing, stating the reasons thereof. Amendment by applicable to obligations issued after Dec.
References in Text note below. The permit and permanent permit records shall indicate that an alternative engineered design was part of the approved installation. C and struck out former subpar. This pressure shall be held for not less than 15 minutes. Roof drains shall conform to or. Voluntarily causing a woman with child to miscarry means voluntarily causing abortion of a pregnant woman. For purposes of this subsection, awith respect to which a deduction is disallowed under section 1091 relating to washof or, or the corresponding provision of prior law, shall not be deemed to be recognized.
The High Court, however, held the acquittal is bad in law, and emphasised that it was an absolute duty of a prospective mother to protect her infant from the very moment of conception A person who aids and facilitates a miscarriage is liable for the abetment of the offence of miscarriage under Section 312 read with Section 109 of the Code, even though the abortion did not take place. A separate overflow drain line shall be connected to the drain pan provided with the equipment. Exterior wall openings shall be made water tight. The final test of the completed drainage and vent systems shall be visual and in sufficient detail to determine compliance with the provisions of this code. Such piping shall maintain a horizontal slope in the direction of discharge of not less than one-eighth unit vertical in 12 units horizontal 1-percent slope. Such guides shall prevent pipe movement in a direction perpendicular to the axis of the pipe.
Where earthquake loads are applicable in accordance with the building code, plumbing piping supports shall be designed and installed for the seismic forces in accordance with the. Vertical leaders shall be sized based on the flow rate from horizontal gutters or the maximum flow rate through roof drains. The registered design professional shall indicate on the permit application that the plumbing system is an alternative engineered design. Piping materials exposed within plenums shall comply with the provisions of the. The registered design professional shall submit to the code official two complete sets of signed and sealed construction documents for the alternative engineering design. Floor drains shall not be connected to a storm drain. The sump pit shall be constructed of tile, steel, plastic, cast iron, concrete or other approved material, with a removable cover adequate to support anticipated loads in the area of use.
Leaders and storm drains connected to a building storm sewer shall not be required to be trapped. The materials and methods utilized for the construction and installation of storm drainage systems shall comply with this section and the applicable provisions of. Individual storm water traps shall be installed on the storm water drain branch serving each conductor, or a single trap shall be installed in the main storm drain just before its connection with the combined building sewer or the public sewer. Truss members and components shall not be cut, drilled, notched, spliced or otherwise altered in any way without written concurrence and approval of a registered design professional. Amendment by applicable to costs incurred after Dec. Secondary roof drain systems shall have the end point of discharge separate from the primary system. For sizes 2 inches and smaller, a guide shall be installed midway between required vertical supports.
Where appliances, equipment or insulation are subject to water damage when auxiliary drain pans fill such portions of the appliances, equipment and insulation shall be installed above the flood level rim of the pan. Where the public sewer is a combined system for both sanitary and storm water, the storm sewer shall be connected independently to the public sewer. Amendment by applicable to distributions after Aug. Water, soil and waste pipes shall not be installed outside of a building, in attics or crawl spaces, concealed in outside walls, or in any other place subjected to freezing temperatures unless adequate provision is made to protect such pipes from freezing by insulation or heat or both. Where the code official determines that the alternative engineered design conforms to the intent of this code, the plumbing system shall be approved.